Just recently purchased TMS-200 Software Thermal Interface Controller and TMS-EB200 Expansion Board from Koolance. I have 2 Bitspower G 1/4" Temperature Sensor Stop Fitting installed in my water loop hooked up to TH1 and TH2 on the TMS-200 board. They both report temperatures in the 68-74 deg Celcius range. This obviously is inaccurate and should be much lower probably around 20-25 deg Celcius. What is the correct offset for these temp sensors in the settings for the TMS-200 software?
http://www.performance-pcs.com/catalog/ ... s_id=24759
Koolance TMS Software & Hardware Interface...
1 post • Page 1 of 1
Users browsing this forum: No registered users and 1 guest